Hard-start kit will increase start-up torque up to 500%.
Increases compressor starting torque for faster recycling.
For tight compressors or low voltage.
For all permanent split capacitor, single phase air conditioning and heat pump systems.
Wired with “Piggy-Back” terminals for easy installation on run capacitors.
For all PSC single-phase motors 115 volt thru 277 volts.
For all air conditioning compressors 1/2 to 10hp.
Mounts easily with either screw or clip.
No wiring changes necessary, just be sure your unit is not already using a hard start kit. Connect two wires from this hard start device in parallel with the run capacitor with one wire on each set of terminals. If all the terminals on the run capacitor are used, then use piggy-back terminals to make the connection. If boosting the compressor, connect only to the run capacitor for the compressor. For dual-run caps, connect to the common (C) terminal and the compressor (H or Herm) terminal. It doesn't matter which wire connects to which terminal,
Compressor Rating BTU: 4000 thru 120,000
Compressor Rating HP: 1/2 thru 10
Operating Voltage (VAC): 115-277
Use hardstart kit only on compressors or fans equipped with a run capacitor.